What readings should you get when Megging a motor?
The rule may be stated: Insulation resistance should be approximately one megohm for each 1,000 volts of operating voltage, with a minimum value of one megohm. For example, a motor rated at 2,400 volts should have a minimum insulation resistance of 2.4 megohms.
What should be the insulation resistance of motor?
It is recommended that the insulation resistance of the motor should at least be 1 MΩ1）, and for the voltage to ground of 200 V, I0r should be 200 μA or below.
What is a good megger test result?
If the megger reads a resistance under 1 (1,000 ohms) on your meter after the initial 60-second interval, the cable has failed and the cable should be removed. If the megger reads a resistance between 1-1.25 on your meter, then the cable passes. Any reading above 1.25 is considered excellent.
What is a bad reading when Megging a motor?
A general rule-of-thumb is 10 Megohm or more.
This is how the test works: DC voltage of 500 or 1000 V is applied between the windings and the ground of the motor. During the measurement and immediately afterwards, some of the terminals carry dangerous voltages and MUST NOT BE TOUCHED.
What is a good megger reading for a 480V motor?
IEEE recommends that for motor starting that the operational voltage, expressed as a meg-ohm value doubled plus 1000 is the minimum meg value for starting. For a 480V motor that would mean . 480Meg x 2= . 960 Meg + 1000, so a minimum ground resistance for starting a 480V is 1.960 Meg or round up to 2 meg-ohms.
How many ohms should a motor read?
With a multimeter, measure the resistance between motor frame (body) and earth. A good motor should read less than 0.5 ohms. Any value greater 0.5 ohms indicate trouble with the motor.
How do you test motor winding resistance?
You should test the windings for a “short to ground” in the circuit and open or shorts in the windings. To test your motor for short to ground, you’ll need to set the multimeter to ohms and disconnect the motor from its power source. Then inspect each wire and look for infinite readings.
How do you Megger a 3 phase motor?
Connect one probe of the megger to the earth connection in the motor. So insulation resistance to earth can be checked then connect the second probe to the first winding and check the value, then do it for the second and third, and if all the values are almost the same then its ok.
How do I know how much my Megger is worth?
Test Voltage for Meggering:
- When AC Voltage is used, The Rule of Thumb is Test Voltage (A.C) = (2X Name Plate Voltage) +1000.
- When DC Voltage is used (Most used in All Megger), Test Voltage (D.C) = (2X Name Plate Voltage).
What does a megohm reading of zero mean?
In the case of a short circuit, the deflection pointer shows ‘zero’ which indicates ‘no’ resistance in the circuit being tested. A Megger consists of an EMF source and voltmeter.